الموضوع: ظاهرة الهالة ( الكورونا Corona )

1. ظاهرة الهالة ( الكورونا Corona )

الأخوة الكرام
السلام عليكم و رحمة الله و بركاته
مشاركة اليوم عبارة عن مقاله عن ظاهرة الهالة او ما تسمى بظاهرة الكورونا التى تظهر نتيجة لعدم انتظام المجال الكهربى فى موسطا ما. و إليكم نص المقال

Corona
Corona is caused by the electric field next to an ****** exceeding the breakdown value for air (or whatever it is immersed in). Since the magnitude of the field is inversely proportional to the radius of curvature, sharper edges break down sooner. The corona starting voltage is typically 30 kV/cm radius. Dust or water particles on the surface of the ****** reduce the corona starting voltage, probably by providing local areas of tighter curvature, and hence higher field stress.

The easiest case to analyze is that of a sphere. The magnitude of the electric field at the surface of a sphere in free space is simply the voltage/radius. Note that if the sphere is near another conductor, the field is no longer uniform, as the charge will redistribute itself towards an adjacent conductor, increasing the field.

Since corona is fundamentally a breakdown phenomenon, it follows Paschen's law: the voltage is a function of pd. Double all the dimensions and halve the gas pressure, and the corona voltage will be pretty much the same.

Corona Surface Factor
The following table gives empirically determined correction factors for various surface conditions. These factors are multiplied by the corona starting voltage (or field) to determine the corrected voltage.

Condition of Conductor ------------------------ m0

New, unwashed -------------------------------- 0.67-0.74
Washed with grease solvent ----------------- 0.91-0.93
Scratch-brushed --------------------------------- 0.88
Buffed ---------------------------------------------- 1.00
Dragged and dusty --------------------------- 0.72-0.75
Weathered (5 months) ---------------------------- 0.95
Weathered at low humidity ---------------------- 0.92
For general design ----------------------------- 0.87-0.90
7 strand concentric lay cable ---------------- 0.83-0.87
19, 37, and 61 strand concentric lay cable -----0.80-0.85

Eliminating or reducing corona
Smoothly radiusing the corners of ******s at high voltages relative to nearby ******s will reduce the local field strength.

Put the sharp corner in something with a higher breakdown strength than air. The trick here is to make sure that you have really got the replacement substance in contact with the conductor. By making the high field occur within a substance with a higher breakdown than the surrounding air, corona can be reduced.

Covering sharp corners with an insulating film increases the corona starting voltage at the points with high E-field stress. Generically known as "corona dope", this is an enamel or polystyrene paints or gels that you can apply. Glyptal is one example, and clear nail polish has also been used. Clear acrylic spray paint is another alternative, although the coating is quite thin.

Potting the entire assembly in an insulator (traditionally paraffin or sulfur were used, silicone RTV is a more popular modern alternative) achieves the same result. Immersing the assembly in oil or other insulating fluids will also work. All of the potting and immersion techniques depend on removing the air or gas bubbles to work. Commercial manufacturers pull a vacuum on the container while the assembly is being potted to facilitate the removal of the air bubbles. Experimenters building polyethylene and aluminum foil capacitors for tesla coils run them at low powers using the electrostatic forces between the plates to vibrate and pump the air bubbles out.

A popular approach to reducing corona on wires is to surrounding the conductor by a semiconducting film or layer of greater radius. This effectively increases the radius of the ******, and hence lowers the field strength. You may not need a huge amount of copper to carry the required current (often micro or milliamps), but you want the diameter of the conductor large enough to reduce the corona. Wire of this type is manufactured by Belden, Rowe-Talley, and Caton, among others.

Field grading rings are often used on high voltage equipment to control the electric field distribution. Rather than rely the field that would exist in free space between two charged conductors, a series of other conductors are interposed at intermediate voltages. The intermediate voltages are derived from a capacitive or resistive divider. A capacitive divider may be a simple as the interelectrode capacitances of the grading rings themselves.

Running the system in a tank at high pressure, or in an insulating gas, will increase the corona starting voltage.

وأى استفسار عن هذا الموضوع عن حاضر

تقبلوا تحياتى

2. مشاركة: ظاهرة الهالة ( الكورونا Corona )

السلام عليكم ورحمة الله وبركاته
برجاء سيدى المهندس / سيد لو تذكر لنا الفرق بين الكورونا الموجبة والسالبة والنبضات المصاحبة وأيهما اكثر , وهل من طريقة لحساب تردد هذه النبضات التى ظهورها يعبر عن بدء التفريغ الجزئى للعوازل , وكذلك ما كيفية عمل الSelf-Stablizing Corona Cables
وشكرا لسعة صدركم

3. رد: ظاهرة الهالة ( الكورونا Corona )

شكر ايا سيدي الفاضل

4. رد: ظاهرة الهالة ( الكورونا Corona )

Thhhhaaaannnk YYYoooouuu

5. رد: ظاهرة الهالة ( الكورونا Corona )

جزاك الله خيرااا بشمهندس سيد

6. رد: ظاهرة الهالة ( الكورونا Corona )

بسم الله الرحمن الرحيم
السلام عليكم ورحمة الله وبركاته
شكراً لك اخي الكريم

7. رد: ظاهرة الهالة ( الكورونا Corona )

السلام عليكم ورحمة الله وبركاته
شكراً لك اخي الكريم

8. رد: ظاهرة الهالة ( الكورونا Corona )

وعليكم السلام ورحمة الله وبركاته
شكرا ً استاذي الكريم .. ظاهرة الهالة من المواضيع التي احب ان اهتم بها

9. رد: ظاهرة الهالة ( الكورونا Corona )

شكراً لك على هذا الشرح الوافى

معلومات الموضوع

الأعضاء الذين يشاهدون هذا الموضوع

الذين يشاهدون الموضوع الآن: 1 (0 من الأعضاء و 1 زائر)

ضوابط المشاركة

• لا تستطيع إضافة مواضيع جديدة
• لا تستطيع الرد على المواضيع
• لا تستطيع إرفاق ملفات
• لا تستطيع تعديل مشاركاتك
•