# الموضوع: EXAMPLE OF VOLTAGE DROP CALCULATION AND CABLE SELECTION

1. ## EXAMPLE OF VOLTAGE DROP CALCULATION AND CABLE SELECTION

Note that these calculation represent under the following considerations .
1. Maximum voltage drop 2.5% from Authority’s Supply
2. Working Voltage 380 volt / 3 PH / 50 Hz.
3. Ambient Air Temperature 50 &ordm; C
4. Cable to be installed fully in Air
5. Cable type DUCAB / XLPE / SWA / PVC
6. Route length 70 Mtr.
7. Two cables will connected parallel in order to carry out one chiller load .
8. Cable Should Cary out Maximum 370.5 Amp. / phase / at 380 volt as per electrical data sheet for our chiller attached.

A - Cable selection for above condition.

- From table 13 . Rating factor for XLPE at 50 &ordm; C = 0.82, which mean that we have to consider that our current capacity should be 370.5 / 0.82 = 452Amp. at 30&ordm; C .
- Appropriate volt drop ( mV ) equation as follows

Vd x 1000
mV = in mV / Amp. / Meter
I x L

- Where Vd : Maximum acceptable volt drop ( in Volt )
- I : Current per phase ( in Amp. )
- L : Route Length ( in Meter )

2.5% x 380 x 1000
mV = = 0.3002 mV / Amp. / Meter
452 x 70

- From table 30. for voltage drop less than 0.3002 and in same time representing the 452Amp. Load required, it will be seen that at voltage drop of 0.255 mV/amp./meter and current of 463Amp., Cable selection could be 4c x 185mm2 .

B – voltage drop calculation in case of using cable size 4c x 300mm2.

- In case of using cable with size 4c x 300mm2 and if we consider a current capacity in range of 452Amp. From table 30. , mV value will be 0.176 mv / amp./ meter ,
- Using same equation above

mV x L x I
Vd = =
1000

0.176 x 70 x 465
Vd = = 5.7288 volt
1000
Vd = (5.7288 volt ) it is 1.50% from total supply , and it is compliance with regulation 525 of the 16th edition of the IEE wiring regulation and with local Authority’ rules

2. ## رد: EXAMPLE OF VOLTAGE DROP CALCULATION AND CABLE SELECTION

شكرا يا بشمهندس فؤاد على هذه المعلومه المفيده جدا
ولكن اين الجدول رقم 30 المشار اليه برجاء رفعه مع مزيد من التفصيل فى هذا الموضوع
بالذات لانه مهم جدا
واريد ايضاح شىء مهم فى حساب مساحه مقطع كابل ليناسب حمل معين لابد من الاخذ فى الاعتبار تيار القصر المتوقع حدوثه فى الكابل

3. ## رد: EXAMPLE OF VOLTAGE DROP CALCULATION AND CABLE SELECTION

المشاركة الأصلية كتبت بواسطة Fouad Sleiman
Note that these calculation represent under the following considerations .
1. Maximum voltage drop 2.5% from Authority’s Supply
2. Working Voltage 380 volt / 3 PH / 50 Hz.
3. Ambient Air Temperature 50 &ordm; C
4. Cable to be installed fully in Air
5. Cable type DUCAB / XLPE / SWA / PVC
6. Route length 70 Mtr.
7. Two cables will connected parallel in order to carry out one chiller load .
8. Cable Should Cary out Maximum 370.5 Amp. / phase / at 380 volt as per electrical data sheet for our chiller attached.

A - Cable selection for above condition.

- From table 13 . Rating factor for XLPE at 50 &ordm; C = 0.82, which mean that we have to consider that our current capacity should be 370.5 / 0.82 = 452Amp. at 30&ordm; C .
- Appropriate volt drop ( mV ) equation as follows

Vd x 1000
mV = in mV / Amp. / Meter
I x L

- Where Vd : Maximum acceptable volt drop ( in Volt )
- I : Current per phase ( in Amp. )
- L : Route Length ( in Meter )

2.5% x 380 x 1000
mV = = 0.3002 mV / Amp. / Meter
452 x 70

- From table 30. for voltage drop less than 0.3002 and in same time representing the 452Amp. Load required, it will be seen that at voltage drop of 0.255 mV/amp./meter and current of 463Amp., Cable selection could be 4c x 185mm2 .

B – voltage drop calculation in case of using cable size 4c x 300mm2.

- In case of using cable with size 4c x 300mm2 and if we consider a current capacity in range of 452Amp. From table 30. , mV value will be 0.176 mv / amp./ meter ,
- Using same equation above

mV x L x I
Vd = =
1000

0.176 x 70 x 465
Vd = = 5.7288 volt
1000

Vd = (5.7288 volt ) it is 1.50% from total supply , and it is compliance with regulation 525 of the 16th edition of the IEE wiring regulation and with local Authority’ rules
الأخ م.فؤاد
السلام عليكم ورحمة الله وبركاته
بارك الله في حسناتك ،وجزاك الله عنا خير الجزاء
ذكرت أن الحمل سيغذي بواسطة كابلين ،على التوازي ،فهل الاستنتاج لحجم الكابل"4X185"،يعني حجم أحد الكابلين المتصلين على التوازي ؟،أي ان الحمل سيغذى بكابلين كل منهما حجمه 185 4X ؟
أذا كان ذلك ماتعنيه ،فاسمح لي أن أنبهك لإعادة حساباتك .
وفقك الله لكل خير

4. ## رد: EXAMPLE OF VOLTAGE DROP CALCULATION AND CABLE SELECTION

السلام عليكم

اولا
اريد معرفة العلاقه بين حساب هبوط الجهد وتيار القصر
ثانيا
اريد طريقة سهله ومبسطه لحساب تيار القصر لشبكه التوزيع
ولكم جزيل الشكر

5. ## رد: EXAMPLE OF VOLTAGE DROP CALCULATION AND CABLE SELECTION

الاخوة الزملاء:

الحسابات المدرجة عن طريق الزميل م /فؤاد سليمان بها اخطاء كثيرة ولا انصح احدا بالاخذ بها ولمعرفة الحسابات الصحيحة تابعوا معى موضوع (اسئل ..لا تتردد..) بقسم التصميم على الرابط

الزميل المهندس/ عبد الله
تم الاجابة على اسئلتك بموضوع (اسئل ..لا تتردد..) بقسم التصميم برجاء زيارة الموضوع والاطلاع على الاجاباتعلى الرابط

تحياتى

6. ## رد: EXAMPLE OF VOLTAGE DROP CALCULATION AND CABLE SELECTION

المشاركة الأصلية كتبت بواسطة Fouad Sleiman
Note that these calculation represent under the following considerations .
1. Maximum voltage drop 2.5% from Authority’s Supply
2. Working Voltage 380 volt / 3 PH / 50 Hz.
3. Ambient Air Temperature 50 &ordm; C
4. Cable to be installed fully in Air
5. Cable type DUCAB / XLPE / SWA / PVC
6. Route length 70 Mtr.
7. Two cables will connected parallel in order to carry out one chiller load .
8. Cable Should Cary out Maximum 370.5 Amp. / phase / at 380 volt as per electrical data sheet for our chiller attached.

A - Cable selection for above condition.

- From table 13 . Rating factor for XLPE at 50 &ordm; C = 0.82, which mean that we have to consider that our current capacity should be 370.5 / 0.82 = 452Amp. at 30&ordm; C .
- Appropriate volt drop ( mV ) equation as follows

Vd x 1000
mV = in mV / Amp. / Meter
I x L

- Where Vd : Maximum acceptable volt drop ( in Volt )
- I : Current per phase ( in Amp. )
- L : Route Length ( in Meter )

2.5% x 380 x 1000
mV = = 0.3002 mV / Amp. / Meter
452 x 70

- From table 30. for voltage drop less than 0.3002 and in same time representing the 452Amp. Load required, it will be seen that at voltage drop of 0.255 mV/amp./meter and current of 463Amp., Cable selection could be 4c x 185mm2 .

B – voltage drop calculation in case of using cable size 4c x 300mm2.

- In case of using cable with size 4c x 300mm2 and if we consider a current capacity in range of 452Amp. From table 30. , mV value will be 0.176 mv / amp./ meter ,
- Using same equation above

mV x L x I
Vd = =
1000

0.176 x 70 x 465
Vd = = 5.7288 volt
1000

Vd = (5.7288 volt ) it is 1.50% from total supply , and it is compliance with regulation 525 of the 16th edition of the IEE wiring regulation and with local Authority’ rules
ممكن كتابة معادلة هبوط الجهد بصوره اوضح
ولك جزيل الشكر

7. ## رد: EXAMPLE OF VOLTAGE DROP CALCULATION AND CABLE SELECTION

اليكم برنامج لحساب ال voltage drop باللغة الفرنسية أرجو أن يستفاد منه

وأرجو تفعيل عضويتى حتى أتمكن من المشاركة فى المنتدى

8. ## Re: EXAMPLE OF VOLTAGE DROP CALCULATION AND CABLE SELECTION

شكرا جزيلا لكم جميعا مشروعي هو يختص بالdrop voltage in transmission lines

9. ## رد: EXAMPLE OF VOLTAGE DROP CALCULATION AND CABLE SELECTION

السلام عليكم ورحمه الله وبركاته
مرفق ملف لحساب هبوط الجهد أرجو أن يكون نافعا

10. ## رد: EXAMPLE OF VOLTAGE DROP CALCULATION AND CABLE SELECTION

جزاكم الله خيرا يا مهندس محمود بس ياريت لو نفس البرنامج باللغة الإنجليزية

#### معلومات الموضوع

##### الأعضاء الذين يشاهدون هذا الموضوع

الذين يشاهدون الموضوع الآن: 1 (0 من الأعضاء و 1 زائر)

#### ضوابط المشاركة

• لا تستطيع إضافة مواضيع جديدة
• لا تستطيع الرد على المواضيع
• لا تستطيع إرفاق ملفات
• لا تستطيع تعديل مشاركاتك
•